Detailed product information
l Great absorbing capability(40KA,60KA), low clamping voltage
l Fast response(≤25ns)
l Any module can be replaced any time, convenient for maintenance and reparation
l Available with double monitoring separation device controlled by thermo fuse and current fuse
l With remote monitoring contacts
l The red window shows failure
l Various protection means can be realized conveniently through the combination structure
Notes: 1.The cross sectional area of grounding wire should be on less than 6.0mm2；and that of zero wire should be no less than 5.0 mm2；remote alarm wires 1.5 mm2 Max.
2. Protective apparatus limiting the current to the extent of less than 60A has to be set for the branch circuit of the product.